Question: I recently purchased a home and I am busily repairing all of the items that were identified by the home inspection.
One of the items on the list is that I have 2 – 15 amp circuit breakers in my distribution panel that have 2 wires on the output. The problem is that I do not have any spare positions to add more breakers. What should I do?
Answer: You have two choices:
- You can add a sub-panel. This is probably the best approach to the problem. A sub-panel will allow you to add the necessary new circuit breakers to handle the circuits that have been doubled up on breakers plus it will give you the ability to expand your electrical circuits at a later date. Secondarily it means that each circuit will have a 15 amp load capability. At this time the two circuits combined can only have a maximum 15 amp load.
- You can install an electrical box outside of the load center. Run the cables that are doubled up on the circuit breaker to the electrical box and then run one cable from the electrical box to the load center. The negative to this set-up is that the total load from the two circuits, because they are combined, can only be 15 amps.
Additional information on installing electrical sub-panels.
Additional information on adding an electrical box to split two wires on a circuit breaker.
- LED/Incandescent Christmas Tree Lights
- Wiring An Electric Hot Water Tank
- High & Low Voltage Cables
- Two Wires On A Breaker
- Grounding Rods & Standby Generators
- Fuse Panel Replacement
- Fuse Keeps Blowing
- Identifying Electrical Circuits
- Noisy Dimmer Switch
- Broken Bulb Socket
- CAT-5 Plenum versus Standard Cable
- Dead Batteries In Smoke Detectors
- Garbage Disposal Switches
- Painting Outdoor Breaker Panels & Meters
- How Does Smart Electrical Meter Work?
- Preventing Power Failure
- Intermittent Electrical Receptacles
- Flickering Lights
- Wiring a Light
- Changing Fuses to Beakers
- Breaker Tripping - Light Switch Is Turned On?
- 12/2 Wire On A 15 Amp Breaker
- Fuse To Circuit Panel Upgrade
- Upgrading An Electrical Service
- Change Circuit Breaker Or Split Power?
- Faulty Ceiling Fan Remote Control